Refer to page 22 for the minimum electrical requirements of a standard distribution type High Voltage Fuse and page 18 for typical pad mounted equipment requirements. The conductor and connector systems shall be designed to meet the National Electrical Safety Code Grade C construction. If the line is constructed in an area designated for future 34. Ground wire is to be covered with plastic molding as required by the National ElectricSafety Code. This cable is for direct buried installation and does not require a separate neutral.
These methods demonstrate the two extremes to accomplish this protection. If a primary cable riser is installed on the same pole as the group operated switch, the option two grounding method page 27 will be required for the switch operating handle. All equipment grounding and the switch operating handle grounding must take place at this pole as shown in option two on page 27. Transformers shall be installed to minimize fire hazards as per National Electric Codearticles 450-21 through 450-27. This installation is the sole responsibility of the customer. We cannot schedule your project for construction until the easement document is signed, notarized, and returned to us. For alternate switch designs maintain the following minimum clearances between the metering cluster and the highest energized component of the switch open or closed.
The closest agencies Distance: 40. The remainder of the trench will also be back-filled with select fill. All guy hardware shall have a minimum 15,000 lb. Each transformer shall be properly protected against unauthorized access, and shall bedesigned and installed to meet the requirements of section 38 of the National ElectricSafety Code. It isrecommended that pre-assembled and pre-adjusted switches mounted on steel oraluminum crossarms or cluster mount be utilized. Local government ordinances may have additional qualificationrequirements for these individuals. If the line is constructed in anarea designated for future 34.
The connectors shall be left at the work site for retrieval by the owner or their contractor. The cable shall beprotected above and below with back-fill free from stones or other material that willdamage the cable. Insulation design and electrical clearancesshall conform to the National Electrical Safety Code. Typical interrupting designs are internal de-ionizinggas quenching devices or external rapid separation devices. The parking stand bracket should accommodate standard feed-thru and standoff insulators, and other similar accessories. The responsibility to have these documents properly executed is yours.
Framing Materials: The transformer pole is to be framed with Fiberglass deadendarms or crossarms of southern yellow pine, Douglas fir or an equivalent. Refer to page 17 for typical pad mounted switchgear, page 18 for the minimum electrical requirements and page 21 for a suggested flat pad installation. Be sure to look at the necessary contract period, rate structure and the retailer's customer service record before signing up for a new plan. By securing the price for energy under such contracts for a period of up to five years, Just Energy's customers reduce or eliminate their exposure to changes in the price of gas and power. Always stay away from downed power lines.
Even lines that appear dead can be energized. Single Pole Interface - For a single pole interface structure, the metering, isolation, protection, and primary cable riser equipment if needed will be located on one pole. To paraphrase, if bare concentric neutral orsemiconducting jacketed cables are direct buried, they can be installed in the trenchwith no intentional separation from the other facilities random lay. Finding the right retail natural gas or electric company is all about finding the company that offers the best plan for you. Switchgear shall have the compartment doors interlocked with the interrupter switch such that the door cannot be opened while the switch is closed and the switch cannot be closed while the door is open. Minimum size ground wire is to be 4 bare copper, solid or stranded, and soft drawn.
The voltage rating on this device will not be less than the phase to phase rating of the circuit to be protected. The transformer should be located away from vehicular trafficor should be suitably guarded from damage. We cannot begin our Electric Service Design Phase Step 3 until we have received all of the information requested above. This is to avoid having energized equipment in compartments that are expected to be deenergized when the main switch is open. Just Energy's business includes the sale of natural gas and electricity to residential and commercial customers through long-term stable rate programs. A separate neutral conductor is required when installing this type of cable.
To help you complete these steps, please use our pdf. Minimum size ground wire is to be 4 bare copper, solid or stranded, and soft drawn. Each sectioncontains the appropriate information and specifications to construct that portion of theservice. After you submit this form, you will receive an email confirming that it was received. If you suspect a natural gas leak, get up, get out, and get away. When crossarms are used, they shall be braced.
Your service cannot be energized until we have been notified by the municipal wiring inspector that the secondary electrical work has been approved. You must call us at least three days before needing the trench inspected. The outline drawings shall show all terminal locations, lightning arrester locations, and base detail for design of the foundation. See page 53 for a typicalcustomer installed riser. After you submit this form, you will receive an email confirming that it was received. Whatever you do, don't make a decision purely based on your rate.